Not getting heat and receiving error code 228 from your Lennox® furnace?
This indicates your furnace couldn’t adjust its pressure switch before starting. As a result, your system will not run for your protection.
Repairing or replacing this part is better left to the Experts at Service Experts Heating & Air Conditioning in Denver. Our NATE-certified technicians are among the elite in the industry. They’re well-equipped to handle all of your heating needs, including fixing a furnace error.
We want you to be completely satisfied with our quality furnace repair in Denver. That’s why we back it with a 100% Satisfaction Guarantee* for a year.
How a Pressure Switch Works
This part plays an important part as your furnace prepares to warm your home.
Here’s what goes on after your thermostat’s call for heat:
- Your furnace’s control board begins running the draft inducer blower motor. This drains combustion gases from the heat exchanger and moves in new gas and air so the burners can fire.
- When the pressure switch senses that sufficient air is being pulled into the burners, it closes and commands the control board to ignite the furnace.
- Your furnace ignites and creates heat.
What Happens When a Pressure Switch Breaks Down
When your pressure switch isn’t operating correctly, you’ll likely hear the fan start and the switch clicking multiple times before the furnace switches off completely. When a part isn’t performing right, your furnace will turn off as a safety precaution.
Your furnace will show you something is incorrect with a red flash from its indicator light, which it uses to present error codes. It uses this red light to flash code, like Morse code.
You may notice fast flashes or an alternating slow flash as it transmits a fault code.
Estimated Repair Cost for Furnace Error Code 228
Before replacing the switch, your Service Experts Heating & Air Conditioning Expert will investigate other parts of your furnace first. Several other issues can also create the error code, like a blocked vent or cracked hose.
The cost to remedy your furnace depends on what’s wrong with it and how long it takes to fix it.
If your pressure switch needs to be replaced, you can expect to pay between $40 to $350.
Start with the Experts at Service Experts Heating & Air Conditioning
If you require furnace repair, turn to the pros from Service Experts Heating & Air Conditioning to check out the fault code and fix the issue to your requirements.
Call us at 303-647-5853 or schedule an appointment online today.